The continuous population growth and the growing number of extreme droughts across the world have led to a great increase in consumption of potable and non-potable water. Conservation of rainwater is becoming critical in parts of the United States to meet the growing water demands. Living in a country where water has always been readily available, most people do not realize that rainwater can be used for nearly all non-potable applications including irrigation, toilet flushing, bathroom sinks, mechanical systems, washing machines, car washing, custodial uses, and many more.
Rainwater harvesting is the collection, conveyance, and storage of rainwater. Systems can be as simple as a rain barrel for garden irrigation at the end of a downspout, or as complex as a domestic potable system or a multiple end-use system at a large corporate campus. ParkUSA’s RainTrooper is a solution for both commercial and residential applications to conserve as much rain as possible to store for future use, and reduce consumption of limited treated municipal water.
High Quality Precast Concrete
High Quality Precast Concrete rainwater storage tanks for underground installation provide the largest selection of tank sizes and configurations. The tanks are especially developed for storing rainwater and are equipped with optional liners or coatings to provide the desired level of water quality for a particular application.
Steel Tanks are recommended for applications where the rainwater storage tanks are in a free-standing position, i.e., in a basement or on a slab above ground. The tanks can be constructed from carbon steel, stainless steel, or galvanized steel.
Rainwater storage tanks constructed of HDPE (High Density Polyethylene) or Fiberglass are available for underground installation in every size from 300 to 20,000 gallons. Above ground tanks are free-standing and require a firm level base. Options include tie-downs and freeze protection.
• The most economical of the material options
• Suitable for all outdoor installations
• Provide for heavy traffic durability.
• Extremely strong and can be coated to prevent corrosion and ensure water quality.
• Ideal for outside storage of rainwater in buildings that wish to display their water conservation efforts.
• Suitable for residential or commercial applications
• Light Weight
• Easy to Install
• Corrosive Resistant for use in chemical or heavy industrial areas
- Precast Concrete, Fiberglass, and Steel Models Available
- Overflow Design Available
- Portable Model Available
- Inlet, Outlet, and Vent Connections
- Easy Installation and Maintenance
- Portable Model Available
- Meets all Building Codes
Regardless of the complexity of the system, the rainwater harvesting system comprises the following basic components:
- Catchment surface - the collection surface from which rainfall runs off, typically a roof structure.
- Gutters and downspouts – The harvested rainwater is conveyed through the roof drains and piping to a single point of discharge.
- Rainwater Filter – At the point of discharge, the rainwater is transferred through a filter that removes large and fine debris. ParkUSA provides the following filters for this purpose:
- Filter Collector (RTX-FILCA) – roofs up to 750 sq.ft.
- Compact Filter (RTX-COMFLT) – roofs up to 2100 sq.ft.
- Volume Filter (RTX-VF) – roofs up to 4500 sq.ft.
- Vortex Fine Filter (RTX-VFF) – roofs up to 32,000 sq.ft.
- Make-Up Water Systems with backflow prevention devices
- Rainwater Storage Tanks, also known as cisterns
A best management practice (BMP) for sizing any rainwater harvesting system is to determine the volume of water that can be captured and stored (the supply) and this should equal or exceed the volume of water used (the demand).
Another factor to consider is the loss if rainwater to first flush, evaporation, splash-out, or overshoot from the gutters in hard rains and leaks. Rough collection surfaces are less efficient at conveying water because water captured in pore spaces tends to be lost to evaporation. Also impacting achievable efficiency is the inability of the system to capture all water during intense rainfall events. For instance, if the flow-through capacity of a filter-type roof washer is exceeded, spillage may occur. Additionally, once storage tanks are full, rainwater is lost as overflow.
Supply: The Rational Method is used to calculate the potential supply of rainwater runoff:
Q = CIA
- Q = Average Monthly Rainwater Runoff Rate from drainage area or Average Monthly Supply (GPM)
- C = Runoff Coefficient, the fraction of rainfall on the drainage area that becomes stormwater runoff. Runoff coefficients can range from as high as 0.80-0.85 (for a well-constructed corrugated-iron roof) to 0.10-0.20 (for a compacted soil surface).
- I = Average Intensity of Rainfall (in/hr)
To solve for the average rainfall intensity, find the annual precipitation for the area then divide by 12 months to determine monthly average and ultimately the monthly supply. Consider seasonal adjustments depending on the application.